By ABB SACE
Read or Download ABB handbook protection and control devices PDF
Best nonfiction_3 books
This publication is a needs to learn for a person wishing to correctly comprehend the faith of Islam. the basics of Tawheed clarifies intimately what Islam ability while it says"ONE GOD" by means of picking out and explaninig examples of the violation of the oneness of God in the cultures and ideology of many cultures, the writer proves Islam to be the single actually and basically monotheistic faith.
- Spain For Dummies, 4th edition (Dummies Travel)
- The Therapeutics of Vampirism in Selected Novels of Anne Rice
- Everybody's Knife Bible 3rd edition : All-New Way to Use and Enjoy Your Knives in the Great Outdoors
- Communications in Mathematical Physics - Volume 193
Extra resources for ABB handbook protection and control devices
2 Trip curves 3 General characteristics 3 General characteristics Trip curve electronic releases Trip curve electronic releases S6 - S7 PR211/P S6 - S7 - S8 PR212/P 104 L-I Functions 0,5 0,4 103 1,5 102 0,4 1,5 4 A 2 D C 102 B 1 103 t [s] 2 D C 0,4-0,5-0,55-0,6-0,65-0,7-0,75-0,80,85-0,875-0,9-0,925-0,95-0,975-1 L-S-I Functions, S inverse short delay (I2t = constant) 0,7 0,95 0,6 0,8 1 0,9 t [s] 104 B 4 1 A 6 6 8 D C 101 8 D 10 101 12 C D C 2 3 B B A A 1 1 10 12 B 4 6 A 8 10 10-2 10-2 10-1 1 1,05 101 Note: for PR211/P-I releases, consider the curves relevant to function I only.
3 Limitation curves A circuit-breaker in which the opening of the contacts occurs after the passage of the peak of the short-circuit current, or in which the trip occurs with the natural passage to zero, allows the system components to be subjected to high stresses, of both thermal and dynamic type. 2 “Main definitions”), which are able to start the opening operation before the short-circuit current has reached its first peak, and to quickly extinguish the arc between the contacts; the following diagram shows the shape of the waves of both the prospective short-circuit current as well as of the limited short-circuit current.
1 of the Standard “Circuits of ASSEMBLIES which are exempted from the verification of the short-circuit withstand strength” states that: 1 1 10 102 103 Irms [kA] “A verification of the short-circuit withstand strength is not required in the following cases. … For ASSEMBLIES protected by current-limiting devices having a cut-off current not exceeding 17 kA at the maximum allowable prospective short-circuit current at the terminals of the incoming circuit of the ASSEMBLY. ” The example above is included among those considered by the Standard: if the circuit-breaker was used as a main breaker in a switchboard to be installed in a point of the plant where the prospective short-circuit current is 40 kA, it would not be necessary to carry out the verification of short-circuit withstand.